The Project Gutenberg eBook of Design of a Steel Railroad Warehouse

This ebook is for the use of anyone anywhere in the United States and most other parts of the world at no cost and with almost no restrictions whatsoever. You may copy it, give it away or re-use it under the terms of the Project Gutenberg License included with this ebook or online at www.gutenberg.org. If you are not located in the United States, you will have to check the laws of the country where you are located before using this eBook.

Title: Design of a Steel Railroad Warehouse

Author: Louis Liston Tallyn

Release date: July 9, 2020 [eBook #62597]

Most recently updated: October 18, 2024

Language: English

Credits: Produced by Richard Tonsing and The Online Distributed

Proofreading Team at https://www.pgdp.net (This file was

produced from images generously made available by The

Internet Archive)

*** START OF THE PROJECT GUTENBERG EBOOK DESIGN OF A STEEL RAILROAD WAREHOUSE ***

Transcriber’s Note:

The cover image was created by the transcriber and is placed in the public domain.

DESIGN

OF A

STEEL RAILROAD WAREHOUSE

BY

LOUIS LISTON TALLYN

THESIS

FOR

DEGREE OF BACHELOR OF SCIENCE

IN

CIVIL ENGINEERING

COLLEGE OF ENGINEERING

UNIVERSITY OF ILLINOIS

1901

UNIVERSITY OF ILLINOIS

May 29, 1901

THIS IS TO CERTIFY THAT THE THESIS PREPARED UNDER MY SUPERVISION BY

Louis Liston Tallyn

ENTITLED Design of a Steel Railroad Warehouse

IS APPROVED BY ME AS FULFILLING THIS PART OF THE REQUIREMENTS FOR THE DEGREE

OF Bachelor of Science in Civil Engineering.

HEAD OF DEPARTMENT OF Civil Engineering.

DESIGN OF A STEEL RAILROAD WAREHOUSE

INTRODUCTION

In choosing a thesis subject I have endeavored to select one that would be of practical use to one in the work that is to follow the college training. I have decided to present the design of a steel railroad warehouse at New Orleans for the Illinois Central Railroad as I am greatly interested in railroad work and intend to make that my speciality and because the design of warehouses has so far received only little consideration, but chiefly because a careful study of such a subject will give a knowledge of steel structural work.

PRINCIPLES APPLICABLE IN THE DESIGN OF RAILROAD WAREHOUSES

Nearly all railroad warehouses are of wood, but if a warehouse were to be built today it is certain that, except for small buildings and in localities where timber is exceptionally cheap, a wooden warehouse would not be considered. At present steel seems to be the material which most nearly approaches the ideal for such structures. This use of steel is due to the increase in the cost of timber and to the decrease in the price of structural steel, which now makes it possible to build a much stronger, a better looking, and more economical structure than would have been possible ten years ago.

With a steel structure a settlement of a couple of inches would not in the least impair its efficiency, as the members would adjust themselves by flexure to meet the new condition. This property of a steel structure is of great advantage where the foundations must be located in soil saturated more or less with water, as would be the case near the sea or a large river. Where brick or stonework is built on such foundations, the masonry would be quite likely to crack.

Large freight houses have in the past fifteen years generally been built with a wooden frame covered with sheathing or corrugated iron, and with wooden or combination roof trusses covered with gravel, tin, iron or some form of patent roofing-felt which is supposed to be fireproof. To cheapen the construction, a flat roof is frequently used; but this style of roof is very hard to make absolutely water-tight. Again, where corrugated iron is used as a roof covering the wind has a tendency to drive the rain up under the iron. It is claimed that tin or iron when used on a building near salt water, deteriorate rapidly and that a gravel roof would be much better; but if the iron or tin is kept well painted, there is little danger of its being attacked in that way. When tin or corrugated iron is used as a roof, the trusses may be built much lighter than when gravel is used.

Freight houses are often built very long, for example, the Illinois Central banana sheds at Cairo, Illinois. Here, as at all long warehouses, the length of train standing on the track becomes excessive, and in switching the work of the “banana hands” is often interrupted, while if a train is made up by loading successive cars, they are sometimes detained longer than is advisable. Fifteen hundred feet is probably as long as a warehouse should be. Freight houses should probably not be more than two hundred feet wide, since otherwise freight taken directly from the cars to the vessels must be trucked too far. On the other hand, where package conveyors are used, this would matter little; and the wide warehouse would have greater floor space for the same cost of construction. If a large amount of freight is loaded direct from the cars to the vessels, it may be well to run a track between the freight house and the pier; but at most docks, unless space is very valuable, such freight will be handled at a pier independent of the warehouse.

Where ground space is valuable, a second story is added. This gives a good space for long-storage freight, where it will be out of the way. When the value of barrel and package elevators come to be properly appreciated, two-story warehouses will be built to a greater extent than now.

Doors are introduced in the sides of the building at intervals to allow the freight to be taken in and out. Where the doors are too close, a great deal of space is occupied by passageways, and is therefore rendered useless for the storage of goods. On the other hand, where the distance between the doors is great, the number of berths for vessels is diminished. In single story warehouses, windows in the sides of the building are usually omitted, and light and ventilation is obtained by skylights in the roof, or sometimes only by transoms over the doors. In double story houses the upper floor is often extended across the track-pit so as to utilize the entire ground space for storage, in which case it is necessary to locate windows in the sides of the lower story. Where this is done the windows must be set so high as not to be blocked by freight piled along the sides of the building. A better design is to omit the floor over the track-pit, which reduces the storage space, but also secures an abundance of light and ventilation for the lower story as well as avoids a costly girder construction over the track-pit.

DESCRIPTION OF SOME WAREHOUSES

Before considering the details of the proposed design, a short description of some railroad warehouses will be given. These are not all sea-board warehouses, but they are good examples of current practice. The descriptions are taken from blue prints sent by the railroads.

Michigan Central Freight House, Grand Rapids, Michigan. This is a single story structure, 480 ft. long, and 48 ft. wide sheathed on the sides with galvanized iron, and roofed with tin. The clear height of the building is 11 ft. 9 in. The bents are 15½ ft. by 16 ft. The 12 × 12 in. wooden columns are supported on stone foundations 4 ft. square, having a depth below the ground of 8½ ft. At the north end, 36 ft. of the structure is two-storied the second story being used for offices, toilet rooms etc. One peculiar thing about this warehouse is that it has what may be called a continuous door system by which an opening may be made at any point along the side of the building.

Union Pacific Railroad Standard. The standard freight house for this road is a one-story structure built of brick laid in lime mortar. The foundation is of rubble laid in cement mortar. Above the ground the masonry is range work with ¼–in. joints. The masonry is built up to the underside of the roof boards between the rafters. The door jams are formed of cast iron columns, on which are placed two nine-inch I beams with cast iron separators, on which the wall is continued to the roof. In the office portion the walls are covered with ¾–in. × ½–in. furring strips. The building is covered with a combination roofing-felt.

Chicago St. Paul Minneapolis & Omaha Railroad. The warehouse at Allouez Bay Docks is 1500 ft. long by 80 ft. wide. The sides are covered with No. 24 corrugated iron, and the roof with tin. The entire building is founded on 10–in. oak piling, with the exception of the fifteen feet towards the bay, which is built upon 12 × 12–inch cribwork. Just inside the doors of the warehouse are six platform scales, three on the west or receiving platform and three on the east or delivery side. The doors are white-pine frames covered with No. 26 corrugated iron.

The warehouse of the same road at Duluth is of the same general type, the main difference being that along the sides of the pier movable inclines or gangways are provided which follow the rise and fall of the water and which can be adjusted to suit any boat whether floating high or low in the water. The principal material used in these buildings is creosoted yellow pine, the caps and stringers being 12 × 12–inch, and the posts 10 × 10–inch. The roof trusses are of white pine.

Atchison Topeka & Santa Fe´ Railroad. The freight houses of this road are much the same as those of the Chicago, St. Paul, Minneapolis and Omaha railroad, except that more pains have been taken with the appearances of the structures.

Mobile and Ohio Railroad. The standard freight house of this road is a double-story frame structure, 560 ft. long by 80 ft. wide, sheathed on the outside with galvanized iron, and roofed with a composition roofing-felt. Two tracks enter the building, one near the side and one in the middle. The former is for freight which requires no storage. By the use of iron joists and girders, the floor of the second story is continued without a break across the track-pit. Freight is transferred from and to the upper story by package elevators.

THE WRITER’S DESIGN

The site for the warehouse has been taken at New Orleans, Louisiana, on the property of the Illinois Central fronting the gulf known as Stuyvesant Docks. The design, however, is adapted to any sea-board town where a great deal of heavy freight is received from railroads for shipment by water, or vice versa. It might also with a few variations be suitable for an inland town.

The warehouse will be 600 ft. long. This length is chosen because it represents the length of wharf available for that purpose. The width of the building will be 148 ft., of which 20 ft. in the center will be occupied by two tracks spaced fifteen feet center to center, which allows an ample passage-way between the tracks and also between the floor and the track.

Load. The size of warehouse having been decided upon, the next thing is to select the proper floor load to be allowed for. This depends upon the class of freight to be expected and also upon the manner of storing it. Passage-ways will at most times be left in the freight for accessibility, which will make some difference in the loading; but as the passageways are likely to be omitted at some time, the unit load should be on the side of safety and cover all contingencies. A load of 250 lbs per. sq. ft. on both the upper and lower floor has been taken in this design, which it is believed will be ample as iron ore, lead, etc., will not be stored here.

Support of Upper Floor. The columns will be spaced 20 ft. apart in the direction of the length of the building, and 15 ft. in the other direction. The girders will run parallel to the length of the building and therefore the girders will be 20 ft. long and the joists 15. The economic length of the girder is somewhat less than 20 ft. but by this spacing of the columns more clear room will be obtained, which is a thing worthy of some consideration.

Roof Trusses. The vertical load on the roof will be taken as 35 lbs. per. sq. ft. of horizontal projection, of which 20 lbs. is supposed to cover the weight of the roof itself, and 15 a possible load due to wind. The horizontal effect of the wind is taken as 30 lbs. per. sq. ft. of the vertical projection. A design was first made in which it was intended to span 60 ft. with one Fink truss, but this required such heavy construction in the truss members, that the span of the trusses was reduced to 30 ft. and a column was projected up through the second story to carry one end of the trusses.

For an elevation of the trusses see Plate III, page 23. The stresses in the several members of the trusses were found by graphical resolution. In many cases a stress was found smaller than would be safely carried by a 2 × 2–inch angle, but on account of riveting a smaller section could not be used. For details of the trusses see Plate III, page 23.

Purlins. The purlins are spaced 7 ft. apart and have a span of 20 feet. This requires rather a heavy purlin, and on account of the length there will be more or less deflection in it; but this will not be in the least detrimental. Five-inch nine-pound channels will be used, and on these will be bolted the nailing pieces.

Roof Covering. Over the purlins will be laid 1½–inch fine sheathing covered with tin. Tin is used in preference to corrugated iron, as it may be soldered so as to be absolutely water-tight. On the underside of the sheathing will be nailed a layer of asbestos to prevent sparks from the engines below setting fire to the woodwork.

Flooring. The flooring for the upper story will be 3–inch well-seasoned long leaf yellow pine surfaced to a thickness and laid with square joints. The floor can safely carry the required load with a span of 4 feet, and therefore the joists will be spaced 4 feet center to center. The joists will be supported by girders which are in turn supported by the columns. The joists will be 15–inch 42 lb. I beams, and the girders 20–inch 65–lb. I beams.

Columns. Only two columns will be designed: one having only a part of the roof to support, and one that supports this column and the load on the upper floor. The first is designated A on Plate III, page 23, and the second B.

Column A. The load due to the weight of truss, wind and snow is 24000 lbs. A column composed of 4 angles 3½ × 2½ × 3

16–in. and 2 × ½–in. lacing will be used. The cross-section is shown in the figure . The moment of inertia about the axis AB = 20.4 × 4 = 81.6 inches, and the distance C, from the center of gravity of the cross section to the most extreme fibre, = 4. The bending moment, M, caused by the wind on the roof = 1,442,000 inch pounds. Substituting these values in the formula M = SI ÷ C and solving for S, we obtain a value of 7100 lbs. per. sq. in. The stress per. sq. in. due to the weight of the trusses = 3300 lbs. Therefore the total stress = 7100 + 3300 = 10400 lbs. per. sq. in. The allowable stress = 16000 − (45 l

v). l

v = 13.7. Therefore the allowable stress = 11400 lbs. per. sq. in.

Column B. The dead load caused by column A is 12 tons, and the load on the column due to the second floor is 41.5 tons, making a total of 53.5 tons. The length of column is 12 ft. Try a column composed of four 3 × ½ in. Z bars laced. Half of the wind pressure on the windward side above the floor is transmitted by the roof and the lateral bracing to the columns on the leeward side of the building, and half is carried directly by the columns on the windward side. The wind pressure to be resisted by 10 columns = 46 × 30 × 20 = 27,600 lbs. The columns being fixed at the base, the total moment of the wind = 27,600 × 12 × 6 = 1,987,200 in. lbs. and the moment resisted by one column = 198,720 in. lbs. I ÷ C for this column = 35.1. By substitution in the equation M = SI ÷ C, S = 2300 lbs. per sq. in (approx.). The area of the column = 9.31 sq. in.; and the stress in the column due to the dead load = 83000 ÷ 9.31 = 8900 lbs. per. sq. in.

The other columns will be stressed less than this one; but this section will be used throughout for the columns on the lower floor.

Wind Bracing. Only the method of designing member AD (see Plate III, page 23) will be explained. The wind pressure to be transmitted = 4800 lbs. The secant of the angle of inclination = 1.06. Therefore the stress in AD = 4800 × 1.06 = 5100 lbs. A ¾–in. round rod will be used.

In the same way the sizes of the members CE, EF, and FG are determined.

Foundation. The maximum load for the column is about 55 tons. The foundation will be built on piling, as experiments made by F. J. Llewellyn—Engineering News, May 11 1899—show that the safe load for the soil at New Orleans is only about 700 lbs. per. sq. ft. Nine piles will be used in supporting each column. The depth of pile necessary to safely support the load will be found by driving a few trial piles and using what is known as the Engineering News formula (Baker’s Masonry Construction page 245) P′ = 2Wh ÷ d + 1, in which P′ = the safe load in tons; and d is the penetration in inches under the last blow. W is the weight of the hammer in tons; and h h is the fall in feet. The piles will be of good quality straight-grained white oak, and before being driven, the entire bark will be stripped off. No pile less than 15 in. at the top will be used. The piles will be spaced 3 ft. center to center. A detail drawing of the foundation is shown in Plate III, page 23. The concrete used in the foundation will be composed of 1 part Louisville Natural cement and 4 parts of sandstone broken to pass a 2½–in. ring, the part passing a ½–in. ring being screened out. The concrete is assumed to have a compressive strength of 10 tons per sq. ft., and then the area of the cast iron base to support the column will be 55 ÷ 10 = 5.5 sq. ft. A base 30 inches square will be used.

The first floor will be composed of 6–inches of concrete made as that for the foundation resting directly on the ground. Over this will be spread ½–in. of neat Portland cement to give the floor an even surface.

CONCLUSION

The writer realizes that he has not treated such details as cornices, gutters, window frames, etc. but time will not permit of a further elaboration of the design.

PLATE-I

PLATE-II

PLATE-III

TRANSCRIBER’S NOTES

1. Silently corrected typographical errors and variations in spelling.

2. Archaic, non-standard, and uncertain spellings retained as printed.

*** END OF THE PROJECT GUTENBERG EBOOK DESIGN OF A STEEL RAILROAD WAREHOUSE ***

Updated editions will replace the previous one—the old editions will be renamed.

Creating the works from print editions not protected by U.S. copyright law means that no one owns a United States copyright in these works, so the Foundation (and you!) can copy and distribute it in the United States without permission and without paying copyright royalties. Special rules, set forth in the General Terms of Use part of this license, apply to copying and distributing Project Gutenberg™ electronic works to protect the PROJECT GUTENBERG™ concept and trademark. Project Gutenberg is a registered trademark, and may not be used if you charge for an eBook, except by following the terms of the trademark license, including paying royalties for use of the Project Gutenberg trademark. If you do not charge anything for copies of this eBook, complying with the trademark license is very easy. You may use this eBook for nearly any purpose such as creation of derivative works, reports, performances and research. Project Gutenberg eBooks may be modified and printed and given away—you may do practically ANYTHING in the United States with eBooks not protected by U.S. copyright law. Redistribution is subject to the trademark license, especially commercial redistribution.

START: FULL LICENSE

THE FULL PROJECT GUTENBERG LICENSE

PLEASE READ THIS BEFORE YOU DISTRIBUTE OR USE THIS WORK

To protect the Project Gutenberg™ mission of promoting the free distribution of electronic works, by using or distributing this work (or any other work associated in any way with the phrase “Project Gutenberg”), you agree to comply with all the terms of the Full Project Gutenberg™ License available with this file or online at www.gutenberg.org/license.

Section 1. General Terms of Use and Redistributing Project Gutenberg™ electronic works

1.A. By reading or using any part of this Project Gutenberg™ electronic work, you indicate that you have read, understand, agree to and accept all the terms of this license and intellectual property (trademark/copyright) agreement. If you do not agree to abide by all the terms of this agreement, you must cease using and return or destroy all copies of Project Gutenberg™ electronic works in your possession. If you paid a fee for obtaining a copy of or access to a Project Gutenberg™ electronic work and you do not agree to be bound by the terms of this agreement, you may obtain a refund from the person or entity to whom you paid the fee as set forth in paragraph 1.E.8.

1.B. “Project Gutenberg” is a registered trademark. It may only be used on or associated in any way with an electronic work by people who agree to be bound by the terms of this agreement. There are a few things that you can do with most Project Gutenberg™ electronic works even without complying with the full terms of this agreement. See paragraph 1.C below. There are a lot of things you can do with Project Gutenberg™ electronic works if you follow the terms of this agreement and help preserve free future access to Project Gutenberg™ electronic works. See paragraph 1.E below.

1.C. The Project Gutenberg Literary Archive Foundation (“the Foundation” or PGLAF), owns a compilation copyright in the collection of Project Gutenberg™ electronic works. Nearly all the individual works in the collection are in the public domain in the United States. If an individual work is unprotected by copyright law in the United States and you are located in the United States, we do not claim a right to prevent you from copying, distributing, performing, displaying or creating derivative works based on the work as long as all references to Project Gutenberg are removed. Of course, we hope that you will support the Project Gutenberg™ mission of promoting free access to electronic works by freely sharing Project Gutenberg™ works in compliance with the terms of this agreement for keeping the Project Gutenberg™ name associated with the work. You can easily comply with the terms of this agreement by keeping this work in the same format with its attached full Project Gutenberg™ License when you share it without charge with others.

1.D. The copyright laws of the place where you are located also govern what you can do with this work. Copyright laws in most countries are in a constant state of change. If you are outside the United States, check the laws of your country in addition to the terms of this agreement before downloading, copying, displaying, performing, distributing or creating derivative works based on this work or any other Project Gutenberg™ work. The Foundation makes no representations concerning the copyright status of any work in any country other than the United States.

1.E. Unless you have removed all references to Project Gutenberg:

1.E.1. The following sentence, with active links to, or other immediate access to, the full Project Gutenberg™ License must appear prominently whenever any copy of a Project Gutenberg™ work (any work on which the phrase “Project Gutenberg” appears, or with which the phrase “Project Gutenberg” is associated) is accessed, displayed, performed, viewed, copied or distributed:

This eBook is for the use of anyone anywhere in the United States and most other parts of the world at no cost and with almost no restrictions whatsoever. You may copy it, give it away or re-use it under the terms of the Project Gutenberg License included with this eBook or online at www.gutenberg.org. If you are not located in the United States, you will have to check the laws of the country where you are located before using this eBook.

1.E.2. If an individual Project Gutenberg™ electronic work is derived from texts not protected by U.S. copyright law (does not contain a notice indicating that it is posted with permission of the copyright holder), the work can be copied and distributed to anyone in the United States without paying any fees or charges. If you are redistributing or providing access to a work with the phrase “Project Gutenberg” associated with or appearing on the work, you must comply either with the requirements of paragraphs 1.E.1 through 1.E.7 or obtain permission for the use of the work and the Project Gutenberg™ trademark as set forth in paragraphs 1.E.8 or 1.E.9.

1.E.3. If an individual Project Gutenberg™ electronic work is posted with the permission of the copyright holder, your use and distribution must comply with both paragraphs 1.E.1 through 1.E.7 and any additional terms imposed by the copyright holder. Additional terms will be linked to the Project Gutenberg™ License for all works posted with the permission of the copyright holder found at the beginning of this work.

1.E.4. Do not unlink or detach or remove the full Project Gutenberg™ License terms from this work, or any files containing a part of this work or any other work associated with Project Gutenberg™.

1.E.5. Do not copy, display, perform, distribute or redistribute this electronic work, or any part of this electronic work, without prominently displaying the sentence set forth in paragraph 1.E.1 with active links or immediate access to the full terms of the Project Gutenberg™ License.

1.E.6. You may convert to and distribute this work in any binary, compressed, marked up, nonproprietary or proprietary form, including any word processing or hypertext form. However, if you provide access to or distribute copies of a Project Gutenberg™ work in a format other than “Plain Vanilla ASCII” or other format used in the official version posted on the official Project Gutenberg™ website (www.gutenberg.org), you must, at no additional cost, fee or expense to the user, provide a copy, a means of exporting a copy, or a means of obtaining a copy upon request, of the work in its original “Plain Vanilla ASCII” or other form. Any alternate format must include the full Project Gutenberg™ License as specified in paragraph 1.E.1.

1.E.7. Do not charge a fee for access to, viewing, displaying, performing, copying or distributing any Project Gutenberg™ works unless you comply with paragraph 1.E.8 or 1.E.9.

1.E.8. You may charge a reasonable fee for copies of or providing access to or distributing Project Gutenberg™ electronic works provided that:

- • You pay a royalty fee of 20% of the gross profits you derive from the use of Project Gutenberg™ works calculated using the method you already use to calculate your applicable taxes. The fee is owed to the owner of the Project Gutenberg™ trademark, but he has agreed to donate royalties under this paragraph to the Project Gutenberg Literary Archive Foundation. Royalty payments must be paid within 60 days following each date on which you prepare (or are legally required to prepare) your periodic tax returns. Royalty payments should be clearly marked as such and sent to the Project Gutenberg Literary Archive Foundation at the address specified in Section 4, “Information about donations to the Project Gutenberg Literary Archive Foundation.”

- • You provide a full refund of any money paid by a user who notifies you in writing (or by e-mail) within 30 days of receipt that s/he does not agree to the terms of the full Project Gutenberg™ License. You must require such a user to return or destroy all copies of the works possessed in a physical medium and discontinue all use of and all access to other copies of Project Gutenberg™ works.

- • You provide, in accordance with paragraph 1.F.3, a full refund of any money paid for a work or a replacement copy, if a defect in the electronic work is discovered and reported to you within 90 days of receipt of the work.

- • You comply with all other terms of this agreement for free distribution of Project Gutenberg™ works.

1.E.9. If you wish to charge a fee or distribute a Project Gutenberg™ electronic work or group of works on different terms than are set forth in this agreement, you must obtain permission in writing from the Project Gutenberg Literary Archive Foundation, the manager of the Project Gutenberg™ trademark. Contact the Foundation as set forth in Section 3 below.

1.F.

1.F.1. Project Gutenberg volunteers and employees expend considerable effort to identify, do copyright research on, transcribe and proofread works not protected by U.S. copyright law in creating the Project Gutenberg™ collection. Despite these efforts, Project Gutenberg™ electronic works, and the medium on which they may be stored, may contain “Defects,” such as, but not limited to, incomplete, inaccurate or corrupt data, transcription errors, a copyright or other intellectual property infringement, a defective or damaged disk or other medium, a computer virus, or computer codes that damage or cannot be read by your equipment.

1.F.2. LIMITED WARRANTY, DISCLAIMER OF DAMAGES - Except for the “Right of Replacement or Refund” described in paragraph 1.F.3, the Project Gutenberg Literary Archive Foundation, the owner of the Project Gutenberg™ trademark, and any other party distributing a Project Gutenberg™ electronic work under this agreement, disclaim all liability to you for damages, costs and expenses, including legal fees. YOU AGREE THAT YOU HAVE NO REMEDIES FOR NEGLIGENCE, STRICT LIABILITY, BREACH OF WARRANTY OR BREACH OF CONTRACT EXCEPT THOSE PROVIDED IN PARAGRAPH 1.F.3. YOU AGREE THAT THE FOUNDATION, THE TRADEMARK OWNER, AND ANY DISTRIBUTOR UNDER THIS AGREEMENT WILL NOT BE LIABLE TO YOU FOR ACTUAL, DIRECT, INDIRECT, CONSEQUENTIAL, PUNITIVE OR INCIDENTAL DAMAGES EVEN IF YOU GIVE NOTICE OF THE POSSIBILITY OF SUCH DAMAGE.

1.F.3. LIMITED RIGHT OF REPLACEMENT OR REFUND - If you discover a defect in this electronic work within 90 days of receiving it, you can receive a refund of the money (if any) you paid for it by sending a written explanation to the person you received the work from. If you received the work on a physical medium, you must return the medium with your written explanation. The person or entity that provided you with the defective work may elect to provide a replacement copy in lieu of a refund. If you received the work electronically, the person or entity providing it to you may choose to give you a second opportunity to receive the work electronically in lieu of a refund. If the second copy is also defective, you may demand a refund in writing without further opportunities to fix the problem.

1.F.4. Except for the limited right of replacement or refund set forth in paragraph 1.F.3, this work is provided to you ‘AS-IS’, WITH NO OTHER WARRANTIES OF ANY KIND, EXPRESS OR IMPLIED, INCLUDING BUT NOT LIMITED TO WARRANTIES OF MERCHANTABILITY OR FITNESS FOR ANY PURPOSE.

1.F.5. Some states do not allow disclaimers of certain implied warranties or the exclusion or limitation of certain types of damages. If any disclaimer or limitation set forth in this agreement violates the law of the state applicable to this agreement, the agreement shall be interpreted to make the maximum disclaimer or limitation permitted by the applicable state law. The invalidity or unenforceability of any provision of this agreement shall not void the remaining provisions.

1.F.6. INDEMNITY - You agree to indemnify and hold the Foundation, the trademark owner, any agent or employee of the Foundation, anyone providing copies of Project Gutenberg™ electronic works in accordance with this agreement, and any volunteers associated with the production, promotion and distribution of Project Gutenberg™ electronic works, harmless from all liability, costs and expenses, including legal fees, that arise directly or indirectly from any of the following which you do or cause to occur: (a) distribution of this or any Project Gutenberg™ work, (b) alteration, modification, or additions or deletions to any Project Gutenberg™ work, and (c) any Defect you cause.

Section 2. Information about the Mission of Project Gutenberg™

Project Gutenberg™ is synonymous with the free distribution of electronic works in formats readable by the widest variety of computers including obsolete, old, middle-aged and new computers. It exists because of the efforts of hundreds of volunteers and donations from people in all walks of life.

Volunteers and financial support to provide volunteers with the assistance they need are critical to reaching Project Gutenberg™’s goals and ensuring that the Project Gutenberg™ collection will remain freely available for generations to come. In 2001, the Project Gutenberg Literary Archive Foundation was created to provide a secure and permanent future for Project Gutenberg™ and future generations. To learn more about the Project Gutenberg Literary Archive Foundation and how your efforts and donations can help, see Sections 3 and 4 and the Foundation information page at www.gutenberg.org.

Section 3. Information about the Project Gutenberg Literary Archive Foundation

The Project Gutenberg Literary Archive Foundation is a non-profit 501(c)(3) educational corporation organized under the laws of the state of Mississippi and granted tax exempt status by the Internal Revenue Service. The Foundation’s EIN or federal tax identification number is 64-6221541. Contributions to the Project Gutenberg Literary Archive Foundation are tax deductible to the full extent permitted by U.S. federal laws and your state’s laws.

The Foundation’s business office is located at 809 North 1500 West, Salt Lake City, UT 84116, (801) 596-1887. Email contact links and up to date contact information can be found at the Foundation’s website and official page at www.gutenberg.org/contact

Section 4. Information about Donations to the Project Gutenberg Literary Archive Foundation

Project Gutenberg™ depends upon and cannot survive without widespread public support and donations to carry out its mission of increasing the number of public domain and licensed works that can be freely distributed in machine-readable form accessible by the widest array of equipment including outdated equipment. Many small donations ($1 to $5,000) are particularly important to maintaining tax exempt status with the IRS.

The Foundation is committed to complying with the laws regulating charities and charitable donations in all 50 states of the United States. Compliance requirements are not uniform and it takes a considerable effort, much paperwork and many fees to meet and keep up with these requirements. We do not solicit donations in locations where we have not received written confirmation of compliance. To SEND DONATIONS or determine the status of compliance for any particular state visit www.gutenberg.org/donate.

While we cannot and do not solicit contributions from states where we have not met the solicitation requirements, we know of no prohibition against accepting unsolicited donations from donors in such states who approach us with offers to donate.

International donations are gratefully accepted, but we cannot make any statements concerning tax treatment of donations received from outside the United States. U.S. laws alone swamp our small staff.

Please check the Project Gutenberg web pages for current donation methods and addresses. Donations are accepted in a number of other ways including checks, online payments and credit card donations. To donate, please visit: www.gutenberg.org/donate.

Section 5. General Information About Project Gutenberg™ electronic works

Professor Michael S. Hart was the originator of the Project Gutenberg™ concept of a library of electronic works that could be freely shared with anyone. For forty years, he produced and distributed Project Gutenberg™ eBooks with only a loose network of volunteer support.

Project Gutenberg™ eBooks are often created from several printed editions, all of which are confirmed as not protected by copyright in the U.S. unless a copyright notice is included. Thus, we do not necessarily keep eBooks in compliance with any particular paper edition.

Most people start at our website which has the main PG search facility: www.gutenberg.org.

This website includes information about Project Gutenberg™, including how to make donations to the Project Gutenberg Literary Archive Foundation, how to help produce our new eBooks, and how to subscribe to our email newsletter to hear about new eBooks.

Table of Contents

DESIGN OF A STEEL RAILROAD WAREHOUSE

INTRODUCTION

PRINCIPLES APPLICABLE IN THE DESIGN OF RAILROAD WAREHOUSES

DESCRIPTION OF SOME WAREHOUSES

THE WRITER’S DESIGN

CONCLUSION

THE FULL PROJECT GUTENBERG LICENSE